The sewage treatment plant of Chadormello steel complex is provided for two different purposes. The consumption of this project includes 136m3/hr for the steel factory (SMP) and 164m3/hr for the direct recovery section, according to the designed conditions.
The raw water entering the system with a capacity of 324m3/hr is the treated effluent of Ardakan city.
In order to achieve an acceptable quality according to the RO input standards, this wastewater needs pre-treatment systems such as coagulation and flocculation and DAF system to reduce oil and grease, suspended matter and turbidity, and then the sludge from DAF is sent to the thickener and dewatering units. Sludge (filter press) is directed.
The purified wastewater from the DAF system is fed by feed pumps to the usual pre-treatment units of the reverse osmosis system (sand and carbon filters).
The water obtained from the backwash of sand and carbon filters is directed to the DAF unit for greater efficiency and reuse.
Before entering the reverse osmosis system, the output water from the sand and carbon filters must pass through the ultrafiltration system to reduce the turbidity and SDI of the water in accordance with the standards of the water entering the reverse osmosis system, which is designed by Absan Zalal Company.
has been taken